Results 1 to 16 of 16

01082008, 08:16 AM #1
formula to calculate static pressure in ducts
hi friends,
can anyone tell me whats the key role of static pressure in ducts how its calculated using formula what will happen if it increase or decrease how to suggest this duct size should have this much static pressure

01082008, 11:28 AM #2
Re: formula to calculate static pressure in ducts
Duct work pressure is combination of static and velocity pressure.
Velocity pressure Pv is produced by speed of air movement
Static pressure s.w.g which maintains flow against restistance.
Total pressure is the sum of the veloicty pressure and the static pressure.
Example
If for a given duct size the if air flow is reduced then velocity pressure will also fall as the air speed will decrease, assuming that all other factors/ parameters dont change.
To measure static presure you need Pitotstatic tube connected to a suitable guage which will give you a reading of static pressure and total pressure and you will see from above that if you subtract the static pressure from the total pressure you will then know the velocity pressure.
Dont know if this helps.
Try and think of it like this. If you have a hose pipe connected to a water supply with the end sealed off then as no water is flowing there can be no velocity pressure an no flow is taking place, but if you drilled a hole in the side of the tube water would come out (static pressure) then as flow starts velocity pressure increases with speed of flow, lots of other factors influence the flow of air, system resistance, condition of components in the system etc.

02082008, 02:33 AM #3
Re: formula to calculate static pressure in ducts
To measure static presure you need Pitotstatic tube connected to a suitable guage which will give you a reading of static pressure and total pressure and you will see from above that if you subtract the static pressure from the total pressure you will then know the velocity pressure.
this is the information i got from your reply thanks for it but what i need is how you will say there should be 200pa,100pa static pressure for the ducts how to calculate this pls i need in depth

02082008, 02:36 AM #4
Re: formula to calculate static pressure in ducts
to calculate dynamic pressure there is a formula iam asking for static pressure

02082008, 02:45 PM #5
Re: formula to calculate static pressure in ducts
Your static pressure will be a function of the compressor / Fan that produces it.
You can measure your static using a pitot tube andReality is an elusion created by alcohol deficiency. Quaff and enjoy. [Yorkshire, UK]

02082008, 04:36 PM #6
Re: formula to calculate static pressure in ducts
There's again not such a formula tot calculate static pressure for ducts.
You must look to the whole circuit and every reduction, bend, turn, airturn will increase your resistance and increase pressure. even increasing speed will increase static pressure.
Your ducts must withstand the static pressure which is inside the ducts.
http://www.mece.ualberta.ca/courses/...08B.pdf#searchIt's better to keep your mouth shut and give the impression that you're stupid than to open it and remove all doubt.

04082008, 01:49 AM #7
Re: formula to calculate static pressure in ducts
thanks for the pdf file peter it is difficult for me to understand due to units conversions anyway ill hope it will be useful for me

04082008, 02:18 AM #8
Re: formula to calculate static pressure in ducts
can you pls provide me the tables peter

04082008, 02:25 AM #9
Re: formula to calculate static pressure in ducts
Static pressure is the measure of the potential energy of a unit of air in the particular cross section of a duct. Air pressure on the duct wall is considered static. Imagine a fan blowing into a completely closed duct; it will create only static pressure because there is no air flow through the duct. A balloon blown up with air is a similar case in which there is only static pressure. If you increase the static pressure in a duct such as with a reducer, the staic pressure will decrease and the velocity pressure will increase.
Total Pressure
Consists of the pressure the air exerts in the direction of flow (Velocity Pressure) plus the pressure air exerts perpendicular to the plenum or container through which the air moves. (static pressure) In other words:
PT = PV + PS
PT = Total Pressure
PV = Velocity Pressure
PS = Static Pressure

18032011, 07:12 AM #10
Re: formula to calculate static pressure in ducts
Please, how to calculate duct size is it have any formula or graph?
Last edited by Josip; 21042011 at 12:08 AM.

04072011, 08:17 AM #11
Re: formula to calculate static pressure in ducts
Duct design in Carrier system design or to start with reccommend the book Principles of Air conditioning by P.N.Ananthanarayanan publisher Tata Mcgraw Hill.Once you understand the basics you can use many of the software to design the ducts.

19072011, 07:11 PM #12
Re: formula to calculate static pressure in ducts
so in plain words:
the more the use of reductions, bends, turns, airturns the more the resistance  so the more the static pressure.
Also the use of Pitotstatic tube you can have the reading.

05092011, 10:28 PM #13
Re: formula to calculate static pressure in ducts
Balaji
long time since done but always read pressures not calculated .... (seeing is believing) ... so used magnehelic gauge
R's chillermanIf the World did not Suck, We would all fall off !

05092011, 10:38 PM #14
Re: formula to calculate static pressure in ducts
instead of hijacking posts and going off at a tangent now ur keeping the threads alive!!!
thats why i questioned the first thread ever postedstill waiting a reply but balaji has probably done the airflow calc and bashed the ducting and its probably due for a duct clean!! hope he allowed for access hatches!!!haha

05092011, 11:11 PM #15
Re: formula to calculate static pressure in ducts
Someones been putting them magic mush in me tea again I think
I clicked whats new & this was there .... uh maybe forum's been on the mush tonight aswell !
R's chillermanIf the World did not Suck, We would all fall off !

05092011, 11:29 PM #16
Re: formula to calculate static pressure in ducts
noah has posted on here he wants to design a beer cooler for his ark,they havent invented beer yet but he thinks its a necessity!haha
posted 200bc!!!!haha
Similar Threads

Compressor loading, cooling, and range of operation.
By Air duster in forum FundamentalsReplies: 10Last Post: 02042008, 08:39 AM 
Benji
By benji in forum Trouble ShootingReplies: 29Last Post: 30012008, 01:25 PM 
Building a wine cabinet
By Rory in forum Technical DiscussionsReplies: 38Last Post: 13072004, 08:28 PM 
Fan Static Pressure
By watana in forum Air ConditioningReplies: 3Last Post: 05102003, 06:43 AM