Th.Mihov

21-01-2017, 10:08 PM

Hello

First of all,excuse my bad english :rolleyes:

Since some time i'm interested in refrigeration and air conditioning.Now i'm reading some books about that,but i'm an electrician by education and by occupation,so many aspects of AC/Refrig. are distant to me.That's why many questions arises in my head while i'm reading,but i can't find answers to all of them.That's why i need to ask someone which have knowledge/experience :).To prove my understandings too.It's hard to me to formulate my questions without numbers,so i will take a real compressor data for example calculations.

For example i'll take small split type air conditioner 18000BTU.Assume it is using this compressor - QXC-30K (http://www.areacooling.co.uk/product/compressor-hermetic-rotary-area/qxc-30k).

My first question is about the needed airflow through the evaporator (assume we are heating the room,so the outdoor unit is the evaporator).The compressor capacity is 18000 BTU,it's displacement is 30.7cm3 and it is running at 2900rpm with R407C refrigerant.

If i am correct the refrigerant flow through the evaporator for 1 minute is

Rfm=2900*30.7=89030cm3 or 0.089m3

than the flow for 1 hour is

Rfh=0.089*60=5.34m3

Assuming the outside temp is 2C and the temperature after the evaporator is 5C (arbitary numbers,i don't know if they are correct).From the properties of the R407 at 5C the density of vapor is Hello

First of all,excuse my bad english :rolleyes:

Since some time i'm interested in refrigeration and air conditioning.Now i'm reading some books about that,but i'm an electrician by education and by occupation,so many aspects of AC/Refrig. are distant to me.That's why many questions arises in my head while i'm reading,but i can't find answers to all of them.That's why i need to ask someone which have knowledge/experience :).To prove my understandings too.It's hard to me to formulate my questions without numbers,so i will take a real compressor data for example calculations.

For example i'll take small split type air conditioner 18000BTU.Assume it is using this compressor - QXC-30K (http://www.areacooling.co.uk/product/compressor-hermetic-rotary-area/qxc-30k).

My first question is about the needed airflow through the evaporator (assume we are heating the room,so the outdoor unit is the evaporator).The compressor capacity is 18000 BTU,it's displacement is 30.7cm3 and it is running at 2900rpm with R407C refrigerant.

If i am correct the refrigerant flow through the evaporator for 1 minute is

Rfm=2900*30.7=89030cm3 or 0.089m3

than the flow for 1 hour is

Rfh=0.089*60=5.34m3

Assuming the outside temp is 2C and the temperature after the evaporator is 5C (arbitary numbers,i don't know if they are correct).From the properties of the R407 Hello

First of all,excuse my bad english :rolleyes:

Since some time i'm interested in refrigeration and air conditioning.Now i'm reading some books about that,but i'm an electrician by education and by occupation,so many aspects of AC/Refrig. are distant to me.That's why many questions arises in my head while i'm reading,but i can't find answers to all of them.That's why i need to ask someone which have knowledge/experience :).To prove my understandings too.It's hard to me to formulate my questions without numbers,so i will take a real compressor data for example calculations.

For example i'll take small split type air conditioner 18000BTU.Assume it is using this compressor - QXC-30K (http://www.areacooling.co.uk/product/compressor-hermetic-rotary-area/qxc-30k).

My first question is about the needed airflow through the evaporator (assume we are heating the room,so the outdoor unit is the evaporator).The compressor capacity is 18000 BTU,it's displacement is 30.7cm3 and it is running at 2900rpm with R407C refrigerant.

If i am correct the refrigerant flow through the evaporator for 1 minute is

Rfm=2900*30.7=89030cm3 or 0.089m3

than the flow for 1 hour is

Rfh=0.089*60=5.34m3

Assuming the outside temp is 2C and the temperature after the evaporator is 5C (arbitary numbers,i don't know if they are correct).From the properties of the R407 at 5C the vapor density is 22.37kg/m3,so

Rmass=22.37*5.34=119.45kg

of refrigerant are evaporated.

Again at 5C the specific enthalpy of the refrigerant (its vapor state) is 416.6 kJ/kg.So to fully evaporate that amount (119.45kg) of refrigerant the energy required is

Hg=119.45*416.6=49 762kJ

According this calculator (http://www.peacesoftware.de/einigewerte/luft_e.html)

at 2C outdoor temp and atmospheric pressure (1bar) the specific enthalpy is 275.416kJ/kg.

So we need

Av=49 762/275.416=180m3 of air.

Does this sound right or not?

Thanks in advance :)

First of all,excuse my bad english :rolleyes:

Since some time i'm interested in refrigeration and air conditioning.Now i'm reading some books about that,but i'm an electrician by education and by occupation,so many aspects of AC/Refrig. are distant to me.That's why many questions arises in my head while i'm reading,but i can't find answers to all of them.That's why i need to ask someone which have knowledge/experience :).To prove my understandings too.It's hard to me to formulate my questions without numbers,so i will take a real compressor data for example calculations.

For example i'll take small split type air conditioner 18000BTU.Assume it is using this compressor - QXC-30K (http://www.areacooling.co.uk/product/compressor-hermetic-rotary-area/qxc-30k).

My first question is about the needed airflow through the evaporator (assume we are heating the room,so the outdoor unit is the evaporator).The compressor capacity is 18000 BTU,it's displacement is 30.7cm3 and it is running at 2900rpm with R407C refrigerant.

If i am correct the refrigerant flow through the evaporator for 1 minute is

Rfm=2900*30.7=89030cm3 or 0.089m3

than the flow for 1 hour is

Rfh=0.089*60=5.34m3

Assuming the outside temp is 2C and the temperature after the evaporator is 5C (arbitary numbers,i don't know if they are correct).From the properties of the R407 at 5C the density of vapor is Hello

First of all,excuse my bad english :rolleyes:

Since some time i'm interested in refrigeration and air conditioning.Now i'm reading some books about that,but i'm an electrician by education and by occupation,so many aspects of AC/Refrig. are distant to me.That's why many questions arises in my head while i'm reading,but i can't find answers to all of them.That's why i need to ask someone which have knowledge/experience :).To prove my understandings too.It's hard to me to formulate my questions without numbers,so i will take a real compressor data for example calculations.

For example i'll take small split type air conditioner 18000BTU.Assume it is using this compressor - QXC-30K (http://www.areacooling.co.uk/product/compressor-hermetic-rotary-area/qxc-30k).

My first question is about the needed airflow through the evaporator (assume we are heating the room,so the outdoor unit is the evaporator).The compressor capacity is 18000 BTU,it's displacement is 30.7cm3 and it is running at 2900rpm with R407C refrigerant.

If i am correct the refrigerant flow through the evaporator for 1 minute is

Rfm=2900*30.7=89030cm3 or 0.089m3

than the flow for 1 hour is

Rfh=0.089*60=5.34m3

Assuming the outside temp is 2C and the temperature after the evaporator is 5C (arbitary numbers,i don't know if they are correct).From the properties of the R407 Hello

First of all,excuse my bad english :rolleyes:

Since some time i'm interested in refrigeration and air conditioning.Now i'm reading some books about that,but i'm an electrician by education and by occupation,so many aspects of AC/Refrig. are distant to me.That's why many questions arises in my head while i'm reading,but i can't find answers to all of them.That's why i need to ask someone which have knowledge/experience :).To prove my understandings too.It's hard to me to formulate my questions without numbers,so i will take a real compressor data for example calculations.

For example i'll take small split type air conditioner 18000BTU.Assume it is using this compressor - QXC-30K (http://www.areacooling.co.uk/product/compressor-hermetic-rotary-area/qxc-30k).

My first question is about the needed airflow through the evaporator (assume we are heating the room,so the outdoor unit is the evaporator).The compressor capacity is 18000 BTU,it's displacement is 30.7cm3 and it is running at 2900rpm with R407C refrigerant.

If i am correct the refrigerant flow through the evaporator for 1 minute is

Rfm=2900*30.7=89030cm3 or 0.089m3

than the flow for 1 hour is

Rfh=0.089*60=5.34m3

Assuming the outside temp is 2C and the temperature after the evaporator is 5C (arbitary numbers,i don't know if they are correct).From the properties of the R407 at 5C the vapor density is 22.37kg/m3,so

Rmass=22.37*5.34=119.45kg

of refrigerant are evaporated.

Again at 5C the specific enthalpy of the refrigerant (its vapor state) is 416.6 kJ/kg.So to fully evaporate that amount (119.45kg) of refrigerant the energy required is

Hg=119.45*416.6=49 762kJ

According this calculator (http://www.peacesoftware.de/einigewerte/luft_e.html)

at 2C outdoor temp and atmospheric pressure (1bar) the specific enthalpy is 275.416kJ/kg.

So we need

Av=49 762/275.416=180m3 of air.

Does this sound right or not?

Thanks in advance :)